This article's tone or style may not reflect the encyclopedic tone used on Wikipedia. (Learn how and when to remove this template message)
Water purification is the process of removing contaminants from a raw water source. The goal is to produce water for a specific purpose with a treatment profile designed to limit the inclusion of specific materials; most water is purified for human consumption (drinking water). Water purification may also be designed for a variety of other purposes, including to meet the requirements of medical, pharmacology, chemical and industrial applications. Methods include, but are not limited to: ultra violet light, filtration, water softening, reverse osmosis, ultrafiltration, molecular stripping, deionization, and carbon treatment.
Water purification may remove: particulate sand; suspended particles of organic materal; Parasites, Giardia; Cryptosporidium; bacteria; algae; virus; fungi; etc. Minerals calcium, silica, magnesium, etc., and Toxic metals lead; copper; chromium; etc. Some purification may be elective in the purification process, including smell (hydrogen sulphide remediation), taste (mineral extraction), and appearance (iron incapsulation).
Governments usually dictate the standards for drinking water quality. These standards will require minimum / maximum set points of contaminants and the inclusion of control elements that produce potable drinking water. Quality standards in many countries require specific amounts of disinfectant (such as chlorine) in the water after it leaves the WTP (Water Treatment Plant), to reduce the risk of re-contamination while the water is in the distribution system.
Ground water (usually supplied as well water) is typically a more economical choice than surface water (from rivers, lakes and streams) as a source for drinking, as it is inherently pre-filtered by the aquifer from which it is extracted. Over large areas of the world, aquifers are recharged as part of the hydrologic cycle. In more arid regions, water from an aquifer will have a limited output and can take thousands of years to recharge. Surface water is locally more abundant where subsurface formations do not function as aquifers; however, ground water is far more abundant than the more-visible surface water. Surface water is a typical raw water source used to make drinking water where it is abundant and where ground water is unavailable or of poor quality. However, it is much more exposed to human activity and its byproducts. As a water source it is carefully monitored for the presence of a variety of contaminants by the WTP operators.
It is not possible to tell whether water is safe to drink just by looking at it. Simple procedures such as boiling or the use of a household charcoal filter are not sufficient for treating all the possible contaminants that may be present in water from an unknown source. Even natural spring water - considered safe for all practical purposes in the 1800s - must now be tested before determining what kind of treatment, if any, is needed. Lab analysis, while expensive, is the only way to obtain the information necessary for deciding on method of purification.
- 1 Sources of drinking water
- 2 pH adjustment
- 3 Sedimentation
- 4 Filtration
- 5 Slow sand filters
- 6 Ultrafiltration
- 7 Disinfection
- 8 Additional treatment options
- 9 Other water purification techniques
- 10 Portable water purification
- 11 Water purification for hydrogen production
- 12 Safety and controversies
- 13 References
- 14 External links
- 15 See also
Sources of drinking water
The water emerging from some deep groundwaters may have fallen as rain many decades, hundreds, thousands or in some cases millions of years ago. Soil and rock layers naturally filter the ground water to a high degree of clarity before it is pumped to the treatment plant. Such water may emerge as springs, artesian springs, or may be extracted from boreholes or wells. Deep ground water is generally of very high bacteriological quality (i.e., pathogenic bacteria such as Campylobacter or the pathogenic protozoa Cryptosporidium and Giardia are typically absent), but the water typically is rich in dissolved solids, especially carbonates and sulphates of calcium and magnesium. Depending on the strata through which the water has flowed, other ions may also be present including chloride, and bicarbonate. There may be a requirement to reduce the iron or manganese content of this water to make it pleasant for drinking, cooking, and laundry use. Disinfection is also required. Where groundwater recharge is practised, it is equivalent to lowland surface waters for treatment purposes.
- Shallow groundwaters: Water emerging from shallow groundwaters is usually abstracted from wells or boreholes. The bacteriological quality can be variable depending on the nature of the catchment. A variety of soluble materials may be present including (rarely) potentially toxic metals such as zinc and copper. Arsenic contamination of groundwater is a serious problem in some areas, notably from shallow wells in Bangladesh and West Bengal in the Ganges Delta.
- Upland lakes and reservoirs: Typically located in the headwaters of river systems, upland reservoirs are usually sited above any human habitation and may be surrounded by a protective zone to restrict the opportunities for contamination. Bacteria and pathogen levels are usually low, but some bacteria, protozoa or algae will be present. Where uplands are forested or peaty, humic acids can colour the water. Many upland sources have low pH which require adjustment.
- Rivers, canals and low land reservoirs: Low land surface waters will have a significant bacterial load and may also contain algae, suspended solids and a variety of dissolved constituents.
- Atmospheric water generation is a new technology that can provide high quality drinking water by extracting water from the air by cooling the air and thus condensing water vapour.
- Rainwater harvesting or fog collection which collect water from the atmosphere can be used especially in areas with significant dry seasons and in areas which experience fog even when there is little rain .
- Pumping and containment - The majority of water must be pumped from its source or directed into pipes or holding tanks. To avoid adding contaminants to the water, this physical infrastructure must be made from appropriate materials and constructed so that accidental contamination does not occur.
- Screening (see also Screen filter) - The first step in purifying surface water is to remove large debris such as sticks, leaves, trash and other large particles which may interfere with subsequent purification steps. Most deep Groundwater does not need screening before other purification steps.
- Storage - Water from rivers may also be stored in bankside reservoirs for periods between a few days and many months to allow natural biological purification to take place. This is especially important if treatment is by slow sand filters. Storage reservoirs also provide a buffer against short periods of drought or to allow water supply to be maintained during transitory pollution incidents in the source river.
- Pre-conditioning - Many waters rich in hardness salts are treated with soda-ash (Sodium carbonate) to precipitate calcium carbonate out utilising the common ion effect.
- Pre-chlorination - In many plants the incoming water was chlorinated to minimise the growth of fouling organisms on the pipe-work and tanks. Because of the potential adverse quality effects (see Chlorine below), this has largely been discontinued.
Widely varied techniques are available to remove the fine solids, micro-organisms and some dissolved inorganic and organic materials. The choice of method will depend on the quality of the water being treated, the cost of the treatment process and the quality standards expected of the processed water.
Distilled water has an average pH of 7 (neither alkaline nor acidic) and sea water has an average pH of 8.3 (slightly alkaline). If the water is acidic (lower than 7), lime or soda ash is added to raise the pH. Lime is the more common of the two additives because it is cheaper, but it also adds to the resulting water hardness. Making the water slightly alkaline ensures that coagulation and flocculation processes work effectively and also helps to minimize the risk of lead being dissolved from lead pipes and lead solder in pipe fittings.
Flocculation is a process which starts with clarifying the water. Clarifying means removing any turbidity or colour so that the water is clear and colourless. Clarification is done by causing a precipitate to form in the water. Initially the precipitate forms as very small particles but as the water is gently stirred, these particles stick together to form bigger particles - this process is sometimes called flocculation. Many of the small particles that were originally present in the raw water absorb onto the surface of these small precipitate particles and so get incorporated into the larger particles that coagulation produces. In this way the coagulated precipitate takes most of the suspended matter out of the water and is then filtered off, generally by passing the mixture through a coarse sand filter or sometimes through a mixture of sand and granulated anthracite (high quality coal). Anthracite, with its high carbon content, is able to absorb much of the organic matter present in solution and this can remove odour and taste from the water. A precipitate that is widely used to clarify water is iron (III) hydroxide. This is formed first by adjusting (if necessary) the pH of the incoming water to above 7 (by adding lime or sodium hydroxide), then by adding a solution of an iron (III) compound such as iron (III) chloride. Iron (III) hydroxide is extremely insoluble and forms even at a pH as low as 7. Aluminum hydroxide is also widely used as the flocculating precipitate.
Water exiting the flocculation basin may enter the sedimentation basin, also called a clarifier or settling basin. It is a large tank with slow flow, allowing floc to settle to the bottom. The sedimentation basin is best located close to the flocculation basin so the transit between does not permit settlement or floc break up. Sedimentation basins can be in the shape of a rectangle, where water flows from end to end, or circular where flow is from the center outward. Sedimentation basin outflow is typically over a weir so only a thin top layer-furthest from the sediment-exits.The amount of floc that settles out of the water is dependent on the time the water spends in the basin and the depth of the basin. The retention time of the water must therefore be balanced against the cost of a larger basin. The minimum clarifier retention time is normally 4 hours. A deep basin will allow more floc to settle out than a shallow basin. This is because large particles settle faster than smaller ones, so large particles bump into and integrate smaller particles as they settle. In effect, large particles sweep vertically though the basin and clean out smaller particles on their way to the bottom.
As particles settle to the bottom of the basin a layer of sludge is formed on the floor of the tank. This layer of sludge must be removed and treated. The amount of sludge that is generated is significant, often 3%-5% of the total volume of water that is treated. The cost of treating and disposing of the sludge can be a significant part of the operating cost of a water treatment plant. The tank may be equipped with mechanical cleaning devices that continually clean the bottom of the tank or the tank can be taken out of service when the bottom needs to be cleaned.
After separating most floc, the water is filtered as the final step to remove remaining suspended particles and unsettled floc. The most common type of filter is a rapid sand filter. Water moves vertically through sand which often has a layer of activated carbon or anthracite coal above the sand. The top layer removes organic compounds, which contribute to taste and odour. The space between sand particles is larger than the smallest suspended particles, so simple filtration is not enough. Most particles pass through surface layers but are trapped in pore spaces or adhere to sand particles. Effective filtration extends into the depth of the filter. This property of the filter is key to its operation: if the top layer of sand were to block all the particles, the filter would quickly clog.
To clean the filter, water is passed quickly upward through the filter, opposite the normal direction (called backflushing or backwashing) to remove embedded particles. Prior to this, compressed air may be blown up through the bottom of the filter to break up the compacted filter media to aid the backwashing process; this is known as air scouring. This contaminated water can be disposed of, along with the sludge from the sedimentation basin, or it can be recycled by mixing with the raw water entering the plant.
Some water treatment plants employ pressure filters. These work on the same principle as rapid gravity filters, differing in that the filter medium is enclosed in a steel vessel and the water is forced through it under pressure.
ADVANTAGES: Filters out much smaller particles than paper and sand filters can. Filters out virtually all particles larger than their specified pore sizes. They are quite thin and so liquids flow through them fairly rapidly. They are reasonably strong and so can withstand pressure differences across them of typically 2-5 atmospheres. They can be cleaned (back flushed) and reused.
Membrane filters are widely used for filtering both drinking water and sewage (for reuse). For drinking water, membrane filters can remove virtually all particles larger than 0.2 um--including Giardia and cryptosporidium. Membrane filters are an effective form of tertiary treatment when it is desired to reuse the water for industry, for limited domestic purposes, or before discharging the water into a river that is used by towns further downstream. They are widely used in industry, particularly for beverage preparation (including bottled water). However no filtration can remove substances that are actually dissolved in the water such as phosphorus, nitrates and heavy metal ions.
Slow sand filters
Slow sand filters may be used where there is sufficient land and space. These rely on biological treatment processes for their action rather than physical filtration. Slow sand filters are carefully constructed using graded layers of sand with the coarsest at the top and finest at the base. Drains at the base convey treated water away for disinfection. Filtration depends on the development of a thin biological layer on the surface of the filter. An effective slow sand filter may remain in service for many weeks or even months if the pre-treatment is well designed and produces an excellent quality of water which physical methods of treatment rarely achieve.
Ultrafiltration membranes are a relatively new development; they use polymer film with chemically formed microscopic pores that can be used in place of granular media to filter water effectively without coagulants. The type of membrane media determines how much pressure is needed to drive the water through and what sizes of micro-organisms can be filtered out.
Active coal can fulfil this role.
Disinfection is normally the last step in purifying drinking water. Water is disinfected to kill any pathogens which pass through the filters. Possible pathogens include viruses, bacteria, including Escherichia coli, Campylobacter and Shigella, and protozoans, including G. lamblia and other Cryptosporidia. In most developed countries, public water supplies are required to maintain a residual disinfecting agent throughout the distribution system, in which water may remain for days before reaching the consumer. Following the introduction of any chemical disinfecting agent, the water is usually held in temporary storage - often called a contact tank or clear well to allow the disinfecting action to complete. is the sanitising of sterilization of water. This is done by adding gaseous dissolved chlorine in the water. Chlorine at a concentration of 1 or 2 ppm destroys bacteria and some viruses. Sufficient chlorine is added to the water (with careful monitoring) to ensure that the concentration stays slightly above 1ppm until the water reaches the end user.
- Chlorination- The most common disinfection method is some form of chlorine or its compounds such as chloramine or chlorine dioxide. Chlorine is a strong oxidant that kills many micro-organisms.
Because chlorine is a toxic gas, there is a danger of a release associated with its use. This problem is avoided by the use of sodium hypochlorite, which is either a relatively inexpensive solid that releases free chlorine when dissolved in water or a liquid (bleach) that is typically generated on site using common salt and high voltage DC. Handling the solid, however, requires greater routine human contact through opening bags and pouring than the use of gas cylinders which are more easily automated. The generation of liquid sodium hypochlorite is both inexpensive and safer than the use of gas or solid chlorine. Both disinfectants are widely used despite their respective drawbacks. One drawback to using chlorine gas or sodium hypochlorite is that they react with organic compounds in the water to form potentially harmful chemical by-products trihalomethanes (THMs) and haloacetic acids (HAAs), both of which are carcinogenic in large quantities and regulated by the United States Environmental Protection Agency (EPA). The formation of THMs and haloacetic acids is minimized by effective removal of as many organics from the water as possible prior to chlorine addition. Although chlorine is effective in killing bacteria, it has limited effectiveness against protozoans that form cysts in water. (Giardia lamblia and Cryptosporidium, both of which are pathogenic).
- Chlorine dioxide is another fast-acting disinfectant. It is, however, rarely used, because it may create excessive amounts of chlorate and chlorite, both of which are regulated to low allowable levels. Chlorine dioxide also poses extreme risks in handling: not only is the gas toxic, but it may spontaneously detonate upon release to the atmosphere in an accident.
- Chloramines are another chlorine-based disinfectant. Although chloramines are not as strong of an oxidant or provide a reliable residual, as compared to chlorine gas or sodium hypochlorite, they are less prone to form THMs or haloacetic acids. It is possible to convert chlorine to chloramine by adding ammonia to the water along with the chlorine: The chlorine and ammonia react to form chloramine. Water distribution systems disinfected with chloramines may experience nitrification, wherein ammonia is used a nitrogen source for bacterial growth, with nitrates being generated as a byproduct.
- Ozone (O3) is a relatively unstable molecule "free radical" of oxygen which readily gives up one atom of oxygen providing a powerful oxidising agent which is toxic to most water borne organisms. It is a very strong, broad spectrum disinfectant that is widely used in Europe. It is an effective method to inactivate harmful protozoans that form cysts. It also works well against almost all other pathogens. Ozone is made by passing oxygen through ultraviolet light or a "cold" electrical discharge. To use ozone as a disinfectant, it must be created on site and added to the water by bubble contact. Some of the advantages of ozone include the production of relatively fewer dangerous by-products (in comparison to chlorination) and the lack of taste and odor produced by ozonation. Although fewer by-products are formed by ozonation, it has been discovered that the use of ozone produces a small amount of the suspected carcinogen Bromate, although little Bromine should be present in treated water. Another one of the main disadvantages of ozone is that it leaves no disinfectant residual in the water. Ozone has been used in drinking water plants since 1906 where the first industrial ozonation plant was built in Nice, France. The U.S. Food and Drug Administration has accepted ozone as being safe; and it is applied as an anti-microbiological agent for the treatment, storage, and processing of foods.
- UV radiation (light) is very effective at inactivating cysts, as long as the water has a low level of colour so the UV can pass through without being absorbed. The main disadvantage to the use of UV radiation is that, like ozone treatment, it leaves no residual disinfectant in the water.
Because neither ozone nor UV radiation leaves a residual disinfectant in the water, it is sometimes necessary to add a residual disinfectant after they are used. This is often done through the addition of chloramines, discussed above as a primary disinfectant. When used in this manner, chloramines provide an effective residual disinfectant with very little of the negative aspects of chlorination.
Additional treatment options
- Fluoridation -in many areas fluoride is added to water for the purpose of preventing tooth decay. This process is referred to as water fluoridation. Fluoride is usually added after the disinfection process. In the United States, fluoridation is usually accomplished by the addition of hexafluorosilicic acid, which decomposes in water, yielding fluoride ions.
- Water conditioning: This is a method of reducing the effects of hard water. Hardness salts are deposited in water systems subject to heating because the decomposition of bicarbonate ions creates carbonate ions which crystalise out of the saturated solution of calcium or magnesium carbonate. Water with high concentrations of hardness salts can be treated with soda ash (sodium carbonate) which precipitates out the excess salts, through the Common-ion effect, producing calcium carbonate of very high purity. The precipitated calcium carbonate is traditionally sold to the manufacturers of toothpaste. Several other methods of industrial and residential water treatment are claimed (without general scientific acceptance) to include the use of magnetic or/and electrical fields reducing the effects of hard water.
- Plumbosolvency reduction: In areas with naturally acidic waters of low conductivity (i.e surface rainfall in upland mountains of igneous rocks), the water may be capable of dissolving lead from any lead pipes that it is carried in. The addition of small quantities of phosphate ion and increasing the pH slightly both assist in greatly reducing plumbo-solvency by creating insoluble lead salts on the inner surfaces of the pipes.
- Radium Removal: Some groundwater sources contain radium, a radioactive chemical element. Typical sources include many groundwater sources north of the Illinois River in Illinois. Radium can be removed by ion exchange, or by water conditioning. The back flush or sludge that is produced is, however, a low-level radioactive waste.
- Fluoride Removal: Although fluoride is added to water in many areas, some areas of the world have excessive levels of natural fluoride in the source water. Excessive levels can be toxic or cause undesirable cosmetic effects such as staining of teeth. One method of reducing fluoride levels is through treatment with activated alumina.
Other water purification techniques
Other popular methods for purifying water, especially for local private supplies are listed below. In some countries some of these methods are also used for large scale municipal supplies. Particularly important are distillation (de-salination of seawater) and reverse osmosis.
- Boiling: Water is heated hot enough and long enough to inactivate or kill micro-organisms that normally live in water at room temperature. Near sea level, a vigorous rolling boil for at least one minute is sufficient. At high altitudes (greater than two kilometers or 5000 feet) three minutes is recommended. In areas where the water is "hard" (that is, containing significant dissolved calcium salts), boiling decomposes the bicarbonate ions, resulting in partial precipitation as calcium carbonate. This is the "fur" that builds up on kettle elements, etc., in hard water areas. With the exception of calcium, boiling does not remove solutes of higher boiling point than water and in fact increases their concentration (due to some water being lost as vapour). Boiling does not leave a residual disinfectant in the water. Therefore, water that has been boiled and then stored for any length of time may have acquired new pathogens.
- Carbon filtering: Charcoal, a form of carbon with a high surface area, absorbs many compounds including some toxic compounds. Water passing through activated charcoal is common in household water filters and fish tanks. Household filters for drinking water sometimes contain silver to release silver ions which have an anti-bacterial effect.
- Distillation involves boiling the water to produce water vapour. The vapour contacts a cool surface where it condenses as a liquid. Because the solutes are not normally vaporised, they remain in the boiling solution. Even distillation does not completely purify water, because of contaminants with similar boiling points and droplets of unvaporised liquid carried with the steam. However, 99.9% pure water can be obtained by distillation. Distillation does not confer any residual disinfectant and the distillation apparatus may be the ideal place to harbour Legionnaires' disease.
- Reverse osmosis: Mechanical pressure is applied to an impure solution to force pure water through a semi-permeable membrane. Reverse osmosis is theoretically the most thorough method of large scale water purification available, although perfect semi-permeable membranes are difficult to create. Unless membranes are well-maintained, algae and other life forms can colonise the membranes.
- Ion exchange: Most common ion exchange systems use a zeolite resin bed to replace unwanted Ca2+ and Mg2+ ions with benign (soap friendly) Na+ or K+ ions. This is the common water softener.
- Electrodeionization: Water is passed between a positive electrode and a negative electrode. Ion selective membranes allow the positive ions to separate from the water toward the negative electrode and the negative ions toward the positive electrode. High purity deionized water results. The water is usually passed through a reverse osmosis unit first to remove non-ionic organic contaminants.
- The use of iron in removing arsenic from water. See Arsenic contamination of groundwater#Water purification solutions.
Portable water purification
Portable techniques for purifying water are used for hiking, camping etc. or for use in rural areas or emergency situations. Common techniques include boiling, disinfection with tablets or ultra-filtration using a small hand pump.
Water purification for hydrogen production
For the small scale production of hydrogen, water purifiers are installed to prevent formation of minerals on the surface of the electrodes and to remove organics and chlorine from utility water. First, the water passes through a 20 micrometre interference (mesh or screen filter) filter to remove sand and dust particles, then a charcoal filter using activated carbon to remove organics and chlorine and, finally, a de-ionizing filter to remove metallic ions. Testing can be done before and after the filter to verify the proper removal of barium, calcium, potassium, magnesium, sodium and silicon.
Another method that is used is reverse osmosis.
Safety and controversies
There has been controversy over the fluoridation of water since the 1930s, when the benefits to dental health were first identified.
Water supplies have sometimes been the subject of concerns over terrorism or actual terrorist threats.
- Masters, Gilbert M. Introduction to Environmental Engineering. 2nd ed. Upper Saddle River, NJ: Prentice Hall, 1998.
- United States EPA Ground and Drinking Water Homepage. EPA Ground and Drinking Water Homepage Visited 12/13/05
- Viessman, Warren, and Mark J. Hammer. Water Supply and Pollution Control. 7th ed. Upper Saddle River, NJ: Prentice Hall, 2005.
- History of water purification techniques
- American Water Works Association
- National Safety Foundation
- Code of Federal Register - CFR Title 21 Part 129 Helpful information and water tank installation instructions
- Appropedia:Water supply and purification methods for emergencies - Appropedia, a wiki focused on sustainable development.
|Wikimedia Commons has media related to Water_purification.|